Type of works: supply of EcoCooling's evaporative coolers.
Fyvie Hall at the University of Westminster and its associate board room was consistently uncomfortable during periods of hot weather. As with all universities the carbon impact of any cooling system needed to be minimized.
Fyvie Hall is a listed building dating back to 1912 which hosted the first public viewing of a motion picture. The room is now used for education and conferences with a capacity of up to 150 people. The design of any cooling system also had to comply with all of the constraints associated with a Grade 1 listed building
Above Fyvie hall is the board room. This is a semi-glazed building with natural ventilation.
Two side discharge EcoCoolers and an extraction system were installed to provide cooling for both rooms. The existing ventilation ducts and openings were utilised to avoid any listed building implications. The EcoCooling air-supply fans are installed with pre- and post-sound attenuation to meet the internal requirement of NC40 and local restrictions.
A combined thermostat and humidistat in each room automatically controls the temperature with a maximum relative humidity. This solution has satisfied the cooling requirements of these rooms. With less than 20% of the energy use and carbon impact of an equivalent refrigeration based cooling system this will contribute to the University of Westminsters Sustainability and Responsibility programme.
View Evaporative space cooling Product Entry View EcoCooling Technical Sales Manual PDF